Organizational Preventive Maintenance Checks and Services
ITEM TO BE
Check drain plugs and cocks for
secure and tight fit.
Check burner head assembly for dam-
Check air hose for dirt or corro-
Check burner nozzle
for carbon and electrodes for carbon de-
Check manifold assembly for damaged
or inoperative pressure relief valve,
cracks, or leaks.
Check ignition cable assembly for
Check blower and motor assembly for
tight mounting hardware.
shutter spring-loader rivet for weak-
Check fuel pump assembly for dam-
age and leaks, service pump assembly
by replacing or cleaning fuel filter.
Check boiler tank assembly for
dents, breaks, cracks, and leaks.
Evacuate to DS or GS maintenance if
any of these conditions are evident.
Service boiler tank and skid by
painting scratched or rusted areas.
Check UV scanner assembly for sight
scanner tube instructions.
scanner mounting is tight.